Question about Heating & Cooling
The reason the compressor starts when you push the contactor in is that you have an "open" in your control voltage. I would suspect that the thermostat was bad - since that is 'usually' the only component you have in that circuit.
Since you indicate this problem 'surfaced' after you had the "start cap" replaced - I might be suspicious of the new start cap and how it's wired in - but "assuming" it is correct I would probably change the thermostat.
Note: as with any Air Conditioner - when you start 'changing parts' you run the risk of changing out a perfectly good part (thus wasting perfectly good money) - so - if possible I would see if I could find someone to electrically trouble-shoot the AC to determine 'exactly' what was causing the problem.
hope this helps
Posted on Jul 29, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 10, 2017 | Heating & Cooling
Jan 10, 2013 | Aqua Flo Aquaflo Flo - Master Xp2 2 Speed...
Aug 30, 2012 | AO Smith 1.5hp Pool Pump Motor 2 Speed Ao...
Aug 30, 2010 | 1990 Ford Thunderbird
Jul 06, 2010 | Intertherm P3RC-030K Air Conditioner
May 07, 2009 | Heating & Cooling
Jan 08, 2009 | Heating & Cooling
Jun 17, 2008 | Goodman Heating & Cooling
27 people viewed this question
Usually answered in minutes!