Question about Weather King 10AJA6001AH Air Conditioner
First,with power off,try to manually turn the fan by hand,it should turn freely and coast to a stop by itself,then if so,there is what they call a "dual-Capacitor" inside the unit and one side of this capacitor is the motor start/run capacitor and they go bad,it is a silver can with 3 terminals marked F/C/H fan/common/hermetics (for the compressor), and will say something like 5uf./35uf at 440 volts A.C. on the body of this component go get a replacement at most electrical outlets
Posted on Jul 28, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 25, 2013 | GE Ovens
Mar 18, 2013 | Dryers
Apr 22, 2010 | 2004 Chevrolet TrailBlazer
Jan 28, 2010 | Refrigerators
Oct 23, 2009 | Heating & Cooling
Sep 22, 2009 | Dryers
Sep 10, 2009 | Hampton Bay 24750 Huntington III Ceiling...
Aug 10, 2009 | 2004 Mitsubishi Montero Sport
120 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: