Question about Whirlwind FH-778 Air Conditioner
A/c is blowing but it is not cool air will freon help or do the whole unit need to be replaced my furnance is in the attic which is heating by gas , was told it would cost 6100.00 to replace
Hi, so you have a central air split system, with the gas furnace in the attic and the condenser outdoors. Unless you had a service tech out and told you your system was shot, you more then likely just have a problem with the outdoor unit. Yes, it may be a freon problem and it needs a charge, or some minor problem in one of the electrical circuits not bringing on the compressor so there would be no cooling. $6,000 sounds about right for a complete system, but I don't believe at all that's what you need. If you are familar with electrical, or you are able to go to the outdoor unit to see if you can hear the compressor running, and the outdoor fan is on, this is the place to start. Look it over, turn the unit on and make sure the blower is coming on in the attic. If so, make sure the outdoor unit is up and running. You can take off a panel and hear the compressor to see if it is on. If so, its very possible it is just low on freon. You will have 2- copper lines coming out of this unit. Place your hand on the large line and see if it is nice and cold and even wet, condensation. The smaller line will be much warmer, even hot if its running ok. If you find that the compressor is on and the line is warm, sounds like it may just be a leak and you should call and get a tech out to check this for you. It may be many things, but check to make sure that what I have told you is ok, and keep me posted. Until we find out what is going on, don't let them tell you you need to install a complete system. I am sure you were just checking. Please give me the model and serial number, and name of the outdoor unit if you would be so kind. And the age and over all condition that you think it may be in, like the last time it was serviced. I will wait to hear back from you, so we can get this up and running.
A/C, Heating, & Refrigeration Contractor.
Posted on Jul 28, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jun 15, 2013 | Heating & Cooling
Jul 26, 2011 | Ruud Matching Split Air Conditioner
Apr 02, 2011 | Refrigerators
Jan 23, 2018 | 2000 Dodge Caravan
Jun 25, 2010 | Dometic Rooftop RV Air Conditioner
Mar 29, 2010 | Dometic 57915531 Air Conditioner
Jun 01, 2009 | 1997 Chevrolet Suburban
Aug 25, 2008 | Dometic Rooftop RV Air Conditioner
Nov 19, 2007 | Heating & Cooling
516 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: