Question about Heating & Cooling
There could be several things wrong. The unit could be undersized but since it worked fine in the beginning, we'll rule that out. There could be a refrigerant leak. Check and see if the evaporator coils (inside furnace) are sweating all the way to the top. The new refrigerant in these units makes it absolutely critical they be charged correctly. The expansion valve also requires adjusting sometimes, if so equipped. Just keep talking to the installers. It sounds like they will eventually get it right for you. Sometimes it takes several trips to get everything adjusted perfectly.
Posted on Jul 28, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Feb 27, 2015 | Carrier 52CQ-312-4 Comfort Series Heat...
Sep 15, 2013 | Goodman CACF048B2A Air Conditioner
May 08, 2011 | Dometic Heating & Cooling
Jun 11, 2010 | Heating & Cooling
Sep 20, 2009 | Heating & Cooling
May 19, 2009 | Goodman CLQ36AR49 Air Conditioner
May 13, 2009 | Goodman CLQ36AR49 Air Conditioner
Dec 19, 2008 | Goodman CLQ36AR49 Air Conditioner
Dec 09, 2008 | Heating & Cooling
55 people viewed this question
Usually answered in minutes!