Question about Heating & Cooling
There could be several things wrong. The unit could be undersized but since it worked fine in the beginning, we'll rule that out. There could be a refrigerant leak. Check and see if the evaporator coils (inside furnace) are sweating all the way to the top. The new refrigerant in these units makes it absolutely critical they be charged correctly. The expansion valve also requires adjusting sometimes, if so equipped. Just keep talking to the installers. It sounds like they will eventually get it right for you. Sometimes it takes several trips to get everything adjusted perfectly.
Posted on Jul 28, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 27, 2015 | Carrier 52CQ-312-4 Comfort Series Heat...
Sep 15, 2013 | Goodman CACF048B2A Air Conditioner
May 08, 2011 | Dometic Heating & Cooling
Jun 11, 2010 | Heating & Cooling
Sep 20, 2009 | Heating & Cooling
May 19, 2009 | Goodman CLQ36AR49 Air Conditioner
May 13, 2009 | Goodman CLQ36AR49 Air Conditioner
Dec 19, 2008 | Goodman CLQ36AR49 Air Conditioner
Dec 09, 2008 | Heating & Cooling
Dec 13, 2017 | Heating & Cooling
55 people viewed this question
Usually answered in minutes!