Question about Northstar Generator 13 Hp, 8000 Watt, Trifuel
Hi Doug. Welcome to FixYa I am Kelly. Download this manual and use the applicable section for troubleshooting your Generator.
What concerns me is you said "there is no current anywhere."
This lead me to believe that given at the time of failure you had a light load on the unit that maybe something simple like a wire has vibrated off a connection somewhere.
Is this a brush type or inverter type generator? If it is a brush type one brush getting hot and moving away from the slip ring assy will cause the exact same symptom.
With the brush block installed you should read a low resistance across the brush block terminals.
If you remove the brush block and one brush is longer than the other one suspect the brush block as the cause.
If it is an inverter type generator there are two types one with an inverter electronics box and the other with one or 2 large capacitors. The one with the large capacitor if the condenser wire has come off or burned, the field will not flash. (Common issue)
There is also a 4 post diode block that must be functioning correctly to have a generator output. There is one terminal 90 deg out from the other three that is the positive terminal. It should read to all other posts in one direction and not at all in the other direction. (meter leads reversed)
This should be enough information for you to isloate the problem. If not just respond here and we can walk through troubleshooting your generator after you have the manual and have done some basic troubleshooting.
Thanks for choosing FixYa.
Posted on Jul 30, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 24, 2015 | Husky Electrical Supplies
Dec 05, 2013 | Northstar North Star Honda 13hp 8000 Ppg...
Feb 18, 2013 | 2002 Honda Civic
Oct 16, 2012 | Coleman Powermate Premium Plus 6250W...
Aug 31, 2011 | Northstar Generator 9 Hp, 5500 Watt,...
Jun 12, 2010 | McCulloch 13HP 338 Cc Portable Generator #...
May 02, 2010 | Northstar Generator 18 Hp, 10,000 Watt,...
Feb 09, 2010 | Northstar Generator 9 Hp, 5500 Watt,...
Apr 02, 2009 | Northstar Generator 9 Hp, 5500 Watt,...
Dec 30, 2008 | Electrical Supplies
Jun 16, 2011 | Northstar Generator 13 Hp, 8000 Watt,...
494 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: