Question about Minuteman PRO1500E/1500VA/1050W/USB/RS232 /AVR 6 BATTERY BACK-UP OUTLETS (0784755151827) UPS System
Close the power Open UPS screw Then remove connection & batteries. set the batteries conect + RED - any colour close Charge one hr. start work.
Posted on Apr 24, 2008
Tips for a great answer:
Jun 04, 2014 | APC BE500U Back-UPS ES 500 (BPAPWBE500U)...
Apr 21, 2014 | APC UPS Battery Backup Systems
Jan 22, 2014 | APC Smart-UPS SUA3000RM2U 3000VA USB &...
Feb 07, 2013 | APC Smart-UPS 2200XL (APCSMART2200XL) UPS...
Dec 30, 2012 | APC Conext 900VA (cnb900) UPS System
Automatic: The UPS performs a self-test automatically when turned on, and every
two weeks thereafter (by default). During the self-test, the UPS briefly operates the
connected equipment on battery.
Manual: Press and hold the button for a few seconds to initiate the self-test
REPLACE BATTERY LED ILLUMINATES
Replace Battery LED flashes and
short beep is emitted every two
seconds to indicate the battery is
Check that the battery connectors are fully engaged.
Weak battery. Allow the battery to recharge for 24 hours. Then, perform a self-test. If the
problem persists after recharging, replace the battery.
Failure of a battery self-test. The UPS emits short beeps for one minute and the Replace Battery LED
illuminates. The UPS repeats the alarm every five hours. Perform the self-test
procedure after the battery has charged for 24 hours to confirm the Replace
Battery condition. The alarm stops and the LED clears if the battery passes the
Sep 09, 2011 | APC Smart-UPS RT 5000VA (SURTD5000XLI) UPS...
Apr 30, 2011 | Tripp Lite Tripplite Omniplus 1000 LCD UPS...
Apr 14, 2010 | Fellowes 99052 UPS 425VA Battery Backup...
Mar 26, 2008 | APC (BE500U-WEB) (BE500UWEB) UPS System
167 people viewed this question
Usually answered in minutes!