Question about Heating & Cooling
My air king 5000 does not go on no green led light comes on it came on the first time i hooked it up and no more after that
Posted on Jan 09, 2010
Yes, I have a solution ! I had this problem and tried all the dip switch settings mentioned in the manual. Eventually I just watched the heating cycle to see what was going on. It did all work properly, the heat came on, the water came on, the heat went off and the water went off when the air cooled off. But the fan continues to run until the furnace is completely cool. A little while after the fan stopped the humidifier water supply came on again and stayed on till the next cycle. Eventually I figured out what was happening was that residual heat from the furnace was drifting back through the supply duct and was warm enough to re-trigger the temperature switch that turns the water on. The solution is simple. Close down the control blade of the duct on the hot air side to about 50% Now there is less likelyhood of warm air drifting back and re-triggering the flow valve. I don't recall of any mention in the manual of how to set this blade control so I guess most people leave it wide open. Anyway, this worked for me.
Posted on Dec 11, 2009
I just fixed mine.
Remove the solenoid and coil from the unit. Disconnect the 24VAC electrical and plumbing etc.
remove the lock from the coil (black part). Its a "U" shaped clip device. This should allow the solenoid to come free. Remove the two screws from the base of the solenoid. Now the armature pin should come out.
Inspect the base (within the solenoid). It has a raised "nipple" where the rubber of the armature "seats" itself. In my case, it had disintegrated on one side, causing a bad seal when the armature was "closed".
Take a small grinder tool and very carefully, grind this (nipple within the solenoid base) so you have an even "face" for the rubber piece of the armature to "seat" against.
enjoy 1) not pouring water down the drain 2) teaching yourself a bit about solenoid valves etc 3) getting to play with your tools. 4) not spending $60+ for a new one of these things 5) experience in knowing how to disassemble/fix it the next time
Posted on Jan 29, 2010
I had same problem and found solenoid valve was fault. What was the valve seat was corroded so bud plunger was not able to shut water off. need to replace solenoid valve assembly. Or buy new one!? Tom
Posted on Feb 27, 2011
While installing the Wait 5000 Humidifier, can you use the 24 volt transformer from the previous Humidifier or do you have to use the transformers provided with the Humidifier
Posted on Dec 05, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 28, 2016 | Humidifiers
Feb 03, 2016 | Heating & Cooling
Dec 29, 2015 | Holmes Sunbeam SCM3501 Cool Mist Console...
Jan 31, 2013 | Aprilaire 400 Humidifier
Mar 07, 2011 | Heating & Cooling
Dec 28, 2009 | Honeywell HE260A1010 Whole House...
Dec 17, 2009 | Aprilaire 550 Humidifier
Jan 04, 2009 | Honeywell Power Humidifier: Furnace...
Nov 10, 2008 | Aprilaire 600 Humidifier
9,584 people viewed this question
Usually answered in minutes!