Question about Heating & Cooling
Hi the place where I stay has a brivis heating system with a brivis networker pAnel the single panel model not the flip one. I got an error service 35 hi Message last night and this morning the LCD panel just had everything on it blinking. Is the problem in the inside contoller Where is the thermostat located
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
On the unit outside there is a button that says "push man. pull auto" if it is set to push man then the fan will go constantly.
Posted on Nov 08, 2009
I had the exact same problem and called 1300brivis. They told me that the error means the thermister needs to be replaced. My unit is also out of warranty but they are still going to come out and fix it.
Posted on May 05, 2010
SOURCE: how to fix error 35
Error 35hi means faulty heating/temperature sensor ( thermistor) in the ducting that needs to be replaced by a Brivis technician. A technician will cost call out (including all labour) + the cost of the part.---------------- The Thermister is in the supply air duct generally about 1-2m from the heater, with wire going back to heater which plugs into the underside of the gray control box. ----------- To get the part and replace it yourself.Its time consuming and it requires proper fitting and proper connection. To order the part, click the link below:--- http://www.brivis.com.au/content.cfm?content=97 ------------- To call brivis technician to replace the part.Please click the link below:---- http://www.brivis.com.au/content.cfm?content=37 ----------- This should help.Thanks.Helpmech.'
Posted on Apr 14, 2011
Tips for a great answer:
Jan 27, 2018 | Heating & Cooling
Apr 25, 2013 | Heating & Cooling
Sep 05, 2010 | Heating & Cooling
Jul 12, 2010 | Heating & Cooling
Jun 29, 2010 | Heating & Cooling
Apr 12, 2010 | Heating & Cooling
Jun 11, 2009 | Heating & Cooling
May 12, 2009 | Heating & Cooling
Jun 01, 2008 | Heating & Cooling
159 people viewed this question
Usually answered in minutes!