Question about Goodman CKL30AR30 Air Conditioner
Posted by Anonymous on
I don't see any reason to change the furnace unless it's an air handler and not a furnace with a coil on top or bottom. And then, the only reason to change the inside unit when you change the outside unit is because it's a R-22 system and your going back with a 410A system. They just discontinued R-22 equipment this year and not a lot are still available. But even if that's the case, the only thing they should have to replace is the coil and maybe the copper line set. That's all I can think of. Hope this helps!
Posted on Aug 01, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Oct 06, 2013 | Goodman Manufacturing Goodman DSZC160601...
Mar 16, 2010 | Goodman CKL60AR60 Air Conditioner
Dec 12, 2009 | Goodman CLQ36AR49 Air Conditioner
Nov 21, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jul 30, 2009 | Goodman CKL24AR24 Air Conditioner
Jun 23, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 21, 2009 | Goodman CLJ30AR32 Air Conditioner
Jun 08, 2009 | Goodman CLQ36AR49 Air Conditioner
Aug 06, 2011 | Goodman CKL30AR30 Air Conditioner
64 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: