Question about Goodman CKL30AR30 Air Conditioner
Posted by Anonymous on
I don't see any reason to change the furnace unless it's an air handler and not a furnace with a coil on top or bottom. And then, the only reason to change the inside unit when you change the outside unit is because it's a R-22 system and your going back with a 410A system. They just discontinued R-22 equipment this year and not a lot are still available. But even if that's the case, the only thing they should have to replace is the coil and maybe the copper line set. That's all I can think of. Hope this helps!
Posted on Aug 01, 2010
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 06, 2013 | Goodman Manufacturing Goodman DSZC160601...
Mar 16, 2010 | Goodman CKL60AR60 Air Conditioner
Dec 12, 2009 | Goodman CLQ36AR49 Air Conditioner
Nov 21, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jul 30, 2009 | Goodman CKL24AR24 Air Conditioner
Jun 23, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 21, 2009 | Goodman CLJ30AR32 Air Conditioner
Jun 08, 2009 | Goodman CLQ36AR49 Air Conditioner
Aug 06, 2011 | Goodman CKL30AR30 Air Conditioner
63 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: