Question about Heating & Cooling
I think you need to slow down and start fresh.
1) You have 115v at Transformer-You are reading from Red to White
2) If that checked out OK are you reading 24v out of Transformer?
3) If yes, remove thermostat wires and put a jumper wire between
R and G. Put the Blower Door Back ON and turn on power
hopefully your fan will come on.
4) If the fan comes on, move the jumper between R and Y, put the
blower door back on and turn on power, indoor fan should come
on as well as the outdoor unit. If the happens you have a problem
with the low voltage wire being broke or a defective thermostat.
5) If none of the above happens and you do not have 24v Between
R and Y or R and G, but you have 24v on the secondary side
of the transformer, you have a defective control board.
Posted on Jul 21, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Aug 02, 2015 | Rheem Classic RANL-024JAZ Single-Stage...
Sep 06, 2014 | Genteq Carrier Tempstar 1/10 Hp 230 A/c...
Mar 22, 2012 | Carrier Heating & Cooling
Sep 01, 2011 | Carrier Heating & Cooling
Jul 13, 2011 | Heating & Cooling
Dec 13, 2010 | Haier HC48C1VAR Central Air Conditioner
Aug 28, 2010 | Goodman Heating & Cooling
Jan 21, 2010 | Heating & Cooling
Aug 09, 2009 | Carrier Heating & Cooling
225 people viewed this question
Usually answered in minutes!