Question about Heating & Cooling
Hi, the problem is in the outdoor unit if the indoor unit comes on and is blowing air. At the unit, you will have a disconnect box, 220 volts. Inside there will be 2- fuses. If you can't see them its because they are behind the plastic cover. You may have blown a fuse. This is where to start. Its best to replace both of them, as if 1 blew the other is close behind it. You say the outdoor unit is doing nothing, this is where the compressor and condenser fan is and if this unit is not running, you will have no cooling. So, find out why by checking for power to this condenser. If you replace the fuses and it starts, take a garden hose, kill the power and wash out the coil. Careful not to bend the aluminum fins with to much pressure. Turn power back on and let it cool. We have to find out why its off and this will be the place to start. Please keep me posted and we can go from there.
A/C, Heating, & Refrigeration Contractor
Posted on Jul 20, 2010
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 04, 2014 | Ruud UAKA030 Air Conditioner
Apr 17, 2014 | Ruud Heating & Cooling
Oct 17, 2013 | Ruud Matching Split Air Conditioner
Apr 18, 2011 | Ruud UAKA030 Air Conditioner
Jun 23, 2010 | Ruud UAKA030 Air Conditioner
May 08, 2010 | Ruud UAKA030 Air Conditioner
Aug 10, 2009 | Ruud UAKA037 Air Conditioner
Jul 06, 2009 | Ruud UBHC Air Conditioner
May 28, 2008 | Ruud Matching Split Air Conditioner
Feb 22, 2018 | Mr. Heater Heating & Cooling
372 people viewed this question
Usually answered in minutes!