Question about Goodman CLQ36AR49 Air Conditioner
Posted by Anonymous on
The problem is in the thermostat wiring. Y1 on an air conditioner, brings on the cooling. On a heat pump, it brings on the compressor, which generally fails to heat mode. The O wire operates the reversing valve, which brings on cooling. If these wires are reversed, or not hooked up, you will not get cooling.
Posted on Jul 19, 2010
As a certified heat pump specialist, I can assure you there are many things that can cause it to run warm or hot in the cooling mode. You have provided insufficient data and information to troubleshoot here. Is the system NEWLY installed. If so. Was it working properly and then all of a sudden started blowing warm air? Previous response regarding the proper 24-volt wiring is one thing I would check. I've had several customers in years past whose pet dogs chewed through the thermostat wire leading to the outdoor unit - and wire nuts fixed the problem. I've also found stuck reversing valves - some were fixed by simply switching the thermostat from Cool to Heat approximately 20 times while others had to be totally replaced. I've also found several customers who simply only needed to change their return air filter, turn the system to Heat for 15 minutes to melt ICE accumulation on their indoor coils, then turn system back to Cool. And, I've found other customers who had either not enough or too much Freon in their system causing problems. So, those are the areas that I, personally, would check on my own heat pump system; and, in that order. Good luck.
Posted on Feb 14, 2015
Also check some units energize in heat some in a.c. if your system worked fine then started blowing heat you could have a bad heat sequencer causing electric heat to run. also the reversing valve in the condenser might have failed otherwise check your tstat and change "o" to "b"
Posted on Oct 30, 2014
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 18, 2017 | Heating & Cooling
Jul 12, 2016 | LG LS186HE 18,500 BTU SingZone WaMounted...
Apr 12, 2015 | Honeywell Heat/Cool Thermostat
Jan 03, 2015 | Midea Heating & Cooling
May 05, 2010 | Heating & Cooling
May 31, 2009 | Ruud UBHC Air Conditioner
Nov 25, 2007 | Goodman CLQ36AR49 Air Conditioner
398 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: