Question about American Standard Heating & Cooling
First, air should not be blowing through the trap. The trap is there to isolate the air and to make sure condensate flow is proper. Start by increasing the depth of the trap. The condensate is going to be relatively cold, in the range of 58 degerees F to the Attic's OH MY GOSH hot. Pick up some foam insulation at your favorite hardware or Big Box lumber yard and insulate the pipe.
Posted on Jul 19, 2010
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 24, 2013 | Hitachi Heating & Cooling
Aug 29, 2012 | Whirlpool Heating & Cooling
Jun 05, 2011 | Carrier 38CKC060 Air Conditioner
Sep 04, 2010 | Heating & Cooling
Jul 17, 2010 | Goodman CKL36AR36 Air Conditioner
Sep 13, 2009 | Heating & Cooling
Aug 27, 2009 | Ruud UAMB Air Conditioner
Jun 15, 2009 | Heating & Cooling
Sep 19, 2007 | Weather King 10AJA6001AH Air Conditioner
138 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: