Question about Goodman CLQ36AR49 Air Conditioner
Posted by Anonymous on
CALL AN EXPERT......THE WIRES AT THE CONDENSER ARE NOT CONNECTED PROPERLY.THE UNIT SHOULD HAVE BEEN VACUUMED/PUMP DOWN BEFORE STARTING UP .POSSIBLE LOW ON REFRIGERANT ALSO.
Posted on Aug 08, 2010
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 14, 2015 | Amana Goodman R-410A Heat Pump Condenser 2...
Feb 13, 2014 | Goodman Manufacturing Hvac Direct R410A...
Jul 10, 2013 | Goodman Manufacturing MSG12CRN1N -...
Aug 03, 2011 | Heating & Cooling
Jul 15, 2011 | Heating & Cooling
Aug 18, 2010 | Heating & Cooling
Jun 07, 2010 | Goodman CLQ36AR49 Air Conditioner
Jul 10, 2008 | Goodman Heating & Cooling
123 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: