Question about Samsung Heating & Cooling
There are few possibilities that has to be checked.
a bad capacitor,contactor,or other electrical device in the compressor power line could also be the problem .
Check for the coils.If they are dirty or very old clean them properly and recheck.Check the compressor connections.Check power to the compressor.If the power is low then there is open circuit between any two terminals on the compressor.Re check all the connections and then see.
If there is 24v at coil of contactor and 240volt at line with contator closed...then [if neither compressor or condensor fan are running]:
1. Faulty contactor or if fan running but no compressor then
2. Faulty run capacitor if compressor running but fan not running then, 3)The fan motor is faulty.
You need to identify if you have both line voltage [240v] and control voltage [24v] at outdoor unit before identifying this as a problem. Thanks. Keep updated for any more query. You can rate this solution and show your appreciation.
Posted on Jul 18, 2010
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 22, 2014 | Honeywell Electronic Programmable...
Aug 20, 2013 | Heating & Cooling
Jun 07, 2013 | GE Zoneline AZ55H07D Air Conditioner
Jun 22, 2011 | Goodman CKL36AR36 Air Conditioner
Jun 16, 2011 | Heating & Cooling
Jun 11, 2011 | Carrier 38CKC036 Air Conditioner
May 28, 2011 | Heating & Cooling
Jun 16, 2010 | Fujitsu 24C1 Air Conditioner
Mar 09, 2010 | Heating & Cooling
Aug 15, 2009 | Mitsubishi Mr. Slim MXZ30TN Air...
158 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: