Question about Goodman Heating & Cooling
Check the capacitor first. Some units have 1 capacitor that runs the fan and compressor and it's possible for one side to go bad. If the capacitor looks swollen then it's probably bad. You can check it with a multimeter or take it to a heating and air supply and they can check it for you. This is a very inexpensive part. If the capacitor is good then you will need to check the compressor windings with an ohmmeter. Let me know what you find.
Posted on Jul 17, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Feb 22, 2018 | Heating & Cooling
Jul 20, 2012 | Heating & Cooling
Jul 03, 2012 | 2002 Ford Mustang
Jun 15, 2010 | Dometic Rooftop RV Air Conditioner
Jan 29, 2010 | Jenny Products Inc F34A-30 30 Gallon 3/4...
Nov 01, 2008 | Dayton Gas Furnace Heater
May 30, 2008 | Maytag Refrigerators
164 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: