Question about Pentair MINIMAX NT TSI IGNITER
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
1. There is air in the gas line. Power down the heater and allow it to try igniting until lockout. If it locks out, repeat the process. Most lines will clear within 4-5 attempts to ignite.
2. A plugged burner orifice. Run a small pipe cleaner in the brass fittings on the burner tray. They may have small webs in them restricting gas flow.
If the unit is a Standard (STD on the plate inside) it has a flame sensor that may also be bad. That sensor is on the end of the single wire that is cloase to the ignitor wire near the burners. Also check for a losse ground wire on the heater.
Posted on Dec 21, 2008
This sounds like you have a problem with your pilot. You can check this with a small mirror to see if their is a spark when you turn it on. If you have any soot build up on the pilot that will stop the spark and keep it from lighting also. If you have a short on your pilot wire this could be the problem also. I hope this helps, good luck.
Posted on Dec 12, 2009
Tips for a great answer:
Jul 04, 2014 | Pentair Minimax NT Heater
Jun 04, 2014 | Pentair Minimax NT Heater
Mar 10, 2017 | Pentair Minimax NT Heater
Nov 22, 2010 | Pentair Minimax NT Heater
Aug 16, 2017 | Pentair Minimax NT Heater
Sep 29, 2017 | Pentair Minimax NT Heater
Nov 09, 2009 | Pentair MINIMAX NT TSI IGNITER
Jul 09, 2009 | Pentair Minimax NT Heater
Jun 09, 2009 | Pentair Minimax NT Heater
Jan 16, 2019 | Pool & Spa
72 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: