Question about Heating & Cooling
Yes, this is a common problem on the domi compact. unfortunately ferroli accept no responsibility if not in warranty period! can be a costly repair..
Posted on Aug 19, 2008
Had this before on this model, ignore the fault codes provided you have checked possible causes given in manual. it is either the thermistor is too close to the heat exchanger on the top left, move it further down the pipe and the fault normally stops. it is the thermistor not overheat sensor as that would induce a fault code. if the fault goes away when the cover is off it is the ignitor lead, sounds strange but electrical leakage is occurring to earth due to the high voltage leaks onto the case,
The mad sparkie (also gas engineer!)
Posted on Jan 07, 2014
Scrap the boiler domi compacts are total ****
Posted on Dec 24, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 25, 2016 | 2005 Ford Taurus
Apr 17, 2014 | Water Heaters
Sep 18, 2013 | Computers & Internet
Dec 30, 2010 | Heating & Cooling
Aug 12, 2009 | 1986 Chevrolet Cavalier 2 Door
Jul 13, 2009 | Fujitsu Heating & Cooling
May 02, 2009 | Goodman GMS90703BXA Heater
Mar 18, 2009 | Water Heaters
Jan 08, 2009 | Heating & Cooling
989 people viewed this question
Usually answered in minutes!