Question about Pentair Master Temp 400000 Btu Gas Pool Heater 460736 ()
Have a pentair 400dv heater was operating ok, then noticed that the power and pressure swithch lights are on but no display, no errror codes and heater will not operate
If the power and pressure swithch lights are on but no display, no errror codes and heater will not operate, the problem is the thermostat.
Check the thermostat if it is not low, if low adjust it. if the problem continues, multimeter to read the meter. If it is not working replace with a new one.
Posted on Jul 17, 2010
Here is a quote from a customer who had this unit and replaced it, and he goes on to say....quote.....
"If it's anything like the Pentair MiniMax NT we had, the best advice is to wrap a chain around it and drag it to the curb. I'll never buy another Pentair Heater!
This unit was in service for exactly one year and when it was removed, it looked like a 30 year old unit. It was that burned out and sooted up.
After numerous errors and several trips out by their service rep. they now tell us that the Minimax NT was just a stopgap fix for a LowNox system at the time and they have now stopped making them.
They replaced our unit with a 200,000 btu Peerless unit that oddly, resembles R2D2 or a shop vac but it's working perfectly so far.
I was impressed to learn that a 200,000 BTU unit on a 50,000 gallon pool keeps up perfectly, 90 degrees F. all the time."
I just through that out there because I found too many complaints all about the same problems and the solutions all seem to elude the replacement of the controller(DDTC) providing you have the correct incoming power and correct wiring of which I am sure the wiring is fine as it recently was working, are you getting 24 v into the panel, if not the transformer may be the culprit, I mean this heater has a lot of issues so you may be doing yourself justice having a repairman work on it..... another item in question can be the therm sensor,( when the thermistor is bad or voltage to the back of the control board drops below 20vac. 9 times out of 10 it is the thermistor or temp sensor)but all indications are the $300.00 control(DDTC).
A soot build up could cause an issue with either gas pressure or gas flow. With the heater fired the pressure into the valve should maintain no less than 6" wc for natural gas 13" for propane. If the pressure is good, it is a good idea to clean the orfices regularly to ensure good gas flow to the burners.
Hope This Helps.
Posted on Jul 17, 2010
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 22, 2015 | Pentair MasterTemp Pool Heater 200, 000...
Sep 05, 2017 | Pentair Pool & Spa
Jun 09, 2013 | Pentair Pool & Spa
May 12, 2012 | Pentair Mastertemp Pool & Spa Heater Dual...
Jun 30, 2017 | Pentair Minimax Ch 400,000 Btu Propane...
May 16, 2010 | Pentair Minimax NT Heater
Dec 28, 2009 | Pentair Minimax Ch 400,000 Btu Propane...
May 17, 2009 | Pentair MAXITHERM 333K BTU PROPANE GAS...
Apr 16, 2009 | Pentair Minimax NT Heater
72 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: