Question about Ruud Handler Air Conditioner
Check your circuit breaker for the indoor fan. If that is ok try turning the indoor fan by hand to see if it rotates freely. If it doesn't it probably needs to be replaced. If that's ok then check the capacitor for the indoor fan. It is probably attached to the fan. You can check it with a multimeter with the capacitor check function or take it to a heating and air supply and they can check it. Also check the fan motor windings. Connect one lead of an ohmmeter to the common leg and the other to the start leg. Check the reading remove the lead from the start leg and connect it to the run leg and see what it reads. Common to start should be higher than common to run. If either indicates an open winding then the motor needs to be replace. Some motors have more than one speed. High speed is usually used for A/C.
Posted on Jul 17, 2010
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 14, 2011 | Turboair TAS-12 Air Conditioner
Dec 13, 2010 | LG LS-L1210CL Mini Split Air Conditioner
Aug 31, 2010 | Heating & Cooling
Jul 15, 2010 | Heating & Cooling
Sep 19, 2009 | Goodman CKL36AR36 Air Conditioner
Jun 26, 2009 | Weather King 10AJA3601AH Air Conditioner
May 25, 2009 | Ruud Central System Air Conditioner
Mar 17, 2009 | Heating & Cooling
Oct 10, 2007 | GE AJCH10ACB Built-In Room Air Cool Unit
107 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: