Question about AmcorAire UCHW-H24AF2 Split System Air Conditioner
Hi, It's drawing too many amps. Could be a shorted wire, bad fan motor, or a bad compressor. It could also be the relay in the outside unit. One side of the relay could not be contacting.
I would pull the disconnect outside and look at the contacts on the relay for burns, bugs, or dirt. You can lightly sand the contact if they look dirty. A meter is handy to check it for conductivity. Then I'd look at my wires for bare wire or burn marks. Unplug the compressor, plug the disconnect back or breaker and see if the fan runs. You can also check the compressor by unplugging the fan and plugging just the compressor in and trying it, but it's likely a waste of time if the fan ran okay by itself.
Posted on Jul 16, 2010
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 13, 2017 | Heating & Cooling
May 11, 2014 | Dometic Rooftop RV Air Conditioner
Feb 14, 2011 | Dryers
Jul 03, 2010 | Goldstar M1003R Air Conditioner
May 03, 2010 | Frigidaire FAA068P7A Air Conditioner
Apr 27, 2010 | RTO Cal Torpedo Pump 7500 Gph
Apr 03, 2010 | RTO Pushmatic 100Amp 2-pole circuit...
May 13, 2009 | GE GTS22KBP Top Freezer Refrigerator
May 02, 2009 | Beckett Corporation Beckett Professional...
Apr 24, 2009 | Maytag MGR6875BK Gas Kitchen Range
76 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: