Question about Heating & Cooling
To enter the adjustment mode, press the UP, DOWN, and I buttons simultaneously for three seconds. Press the I button until the feature requiring adjustment is displayed:
HL High Limit.
LL Low Limit.
Ldf Low Limit differential.
Then press the UP and/or DOWN buttons to move the set point to
the desired value. After 60 seconds without any button inputs, the
control will automatically return to the READ mode.
(copied from honeywell's instructions)
to clarify the differential is cut in minus the cut out.
Hope i can be some help to you.
Posted on Apr 21, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 12, 2014 | Water Heaters
Feb 02, 2013 | Water Heaters
Jan 25, 2013 | Heating & Cooling
Nov 22, 2012 | General Electric GE SmartWater Household...
Jun 06, 2011 | Honeywell L4103A1019 combination aquastat....
Feb 19, 2011 | Heating & Cooling
Jan 29, 2010 | Honeywell L4103A1019 combination aquastat....
Nov 03, 2009 | Honeywell Electronic Programmable...
Jan 12, 2009 | Water Heaters
Jun 08, 2008 | Honeywell Heating & Cooling
209 people viewed this question
Usually answered in minutes!