Question about Goodman GMS90703BXA Heater
I have a goodman gms9/gcs9 furnace
i have a problem where the
fuse blow each time I turn on air check for shorts tranformer wiring between thermistat and wiring from circuit board to compressor
all check out ok no shorted conditions
hoever fuse on the boarde still blows when turned on
what do you thing problem area could be
Disconnect the thernostat wires from the control board. Put a jumper wire between R & G put door back on and turn on power. Blower motor
should run, if it blows the fuse then you have a direct short between R &
G at the board. Do this with R and W(heat) and R & Y(cool).
By disconnecting the thermostat wires and reinserting them make sure that they do not touch when inserted into each terminal. If it still blows
that little 3amp fuse when jumpering between each sequence as mentioned above, then I think your board is bad. When Jumpering out the Y terminal you will have to have the AC wires still hooked up. If it
blows the fuse in that sequence. Disconnect the wires out at the condensor.
You mat have a bad contactor at the outdoor unit.
Posted on Jul 16, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Feb 19, 2018 | Goodman Heating & Cooling
Oct 27, 2013 | Goodman GMS90703BXA Heater
Apr 24, 2013 | Goodman GMS90703BXA Heater
Feb 12, 2018 | Goodman GMS90703BXA Heater
Dec 17, 2017 | Goodman Heating & Cooling
Apr 04, 2012 | Goodman Heating & Cooling
Apr 04, 2011 | Goodman Heating & Cooling
May 26, 2010 | Goodman CLQ36AR49 Air Conditioner
Jan 02, 2010 | Goodman GMS90703BXA Heater
Jan 28, 2009 | Goodman GMS90703BXA Heater
266 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: