Question about Carrier 38CKC036 Air Conditioner
The condenser fan runs backwards,
YOU COULD HAVE A BAD RUN CAPACITOR. UNFORTUNITALY THERE UNITE USE A DUAL PURPOSE CAPACITIOR. 40 UFD FOR THE COMPRESSOR AND 4 OR 5 UFD FOR THE FAN. SOMETIMES WHEN THE 4 OR 5 UFD CAPACITOR GOES BAD THE FAN CAN RUN BACKWARDS AND MORE SLOWLY. TRY SHUTTING THE UNIT DOWN AT THE DISCONNECT WAIT 5 MINUTES AND WHEN YOU RESTORE POWER USE A SCREWDRIVER TO GIVE THE FAN A PUSH IN THE CORRECT DIRECTION. IF IT DOES RUN IN THE CORRECT DIRECTION, TRY REPLACING THE CAPACITOR.
Posted on Jun 23, 2010
Sounds like you had a condenser fan replaced ok you just have verify if the fan is a reversible one there is like a plug type connector on top of fan all you have to do is swap the position of the plug ex. if black / white to white/black that changes the rotation. check against the diagram it should be for the CCW position.
Posted on Apr 21, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 19, 2016 | Carrier Heating & Cooling
Jan 15, 2015 | Carrier Heating & Cooling
Sep 23, 2013 | Carrier Packaged A/c 3 Ton 13 Seer And...
Sep 24, 2011 | Carrier 38CKC036 Air Conditioner
Aug 21, 2010 | Carrier 38CKC036 Air Conditioner
Jun 02, 2010 | Carrier 38CKC042 Air Conditioner
Apr 15, 2010 | Carrier Heating & Cooling
Mar 10, 2010 | Carrier Heating & Cooling
Jan 21, 2010 | Carrier Heating & Cooling
Jul 09, 2008 | Carrier 38CKC042 Air Conditioner
Jun 25, 2014 | Carrier 38CKC036 Air Conditioner
Jun 13, 2014 | Carrier 38CKC036 Air Conditioner
307 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: