Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I recommend getting electric back up heat to fix your problem. Like the other gentleman said, defrost is having to kick on too much. It's doing the best it can givin the conditions outside. If you don't have enough power supply for electric back up heat, then a gas furnace or propane furnace will work also, depending on your needs. Heat Pumps are a like a full time fan, they are designed to heat your home at a steady rate unlike forced gas units that turn on extremely high temps and then shut off... Ensure your charge is correct, givin your tempatures the unit sounds to be working correctly, however a second opinion is always a good piece of mind before you spend money on emergency heat.. Hope that helps..
Posted on Dec 02, 2008
if no cold blowing,evaporator is not working,have you ever heard compressor is running,check this out,no compression of course you dont have cool on evaporator.if the compressor is running check the oprating current,if still have enough freon charge,if not running check thermostat reset setting on the coldest,ifn still not run check overload relay on panel control reset lever to put back compressor to run,check condensing fan if working,if not check also over load protection,this should be done by ac tech nician.have a nice day,dont gorget to rate me, thank's
Posted on Apr 18, 2009
i have an E3 error reading on my 12000 btu home airconditioner.Please let me know how to resolve this problem and get the aorcon up and running again .Thank you
Kind regards. Osman
Posted on Mar 22, 2010
5 flashing is ' compressor drive' and check the high pressure, condenser fan motor capacitor for proper running
Posted on May 21, 2010
Tips for a great answer:
Sep 30, 2015 | Inverter Heating & Cooling
Jan 04, 2015 | Heating & Cooling
Nov 10, 2014 | Cfm Daikin R410a Split System Air...
Oct 06, 2014 | Computers & Internet
Jul 21, 2014 | Daikin Mini Split Concealed Duct Units
May 04, 2013 | Daikin RXYMQ48MVJU, VRV-S Air Cooled Eight...
Sep 19, 2012 | Daikin Heating & Cooling
Feb 16, 2011 | Heating & Cooling
Nov 03, 2010 | Cfm Daikin R410a Split System Air...
86 people viewed this question
Usually answered in minutes!