Question about Heating & Cooling
Hi, what you need to do first is to go to the indoor unit and remove the panels where the beeps you are hearing are located. If the power shuts off when you remove the panel, you will have a panel switch located around the perimeter you may have to tape down to restore power while you check it out. You may have a chart on the panel glued to the inside or somewhere that may tell you what is going on according to how many beeps or led light flashes. The condenser coil outside may be shutting off on high head pressure due to it being dirty. You can use a water hose and cut power, and wash the coil out good. Be careful not to use to much pressure or you could bend the aluminum coil. If you are getting two beeps from the indoor unit, and it will not start, it should say on a chart what this means. Make sure your filter is clean. This unit is shutting down on a safety due to something going on, this is why you need to service it, clean coil, make sure filter is clean, Make sure your high voltage connections at all breaker boxes and fuse box at the outdoor unit are good and tight. They may be loose causing the unit to draw to much amperage. Start from the basics and see what happens. It doesn' sound like a internal problem, but I won't rule this out. Do the things as i have asked and we will go from there. Keep me posted.
A/C, Heating, and Refrigeration Contractor.
Posted on Jul 14, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 08, 2013 | Heating & Cooling
Oct 10, 2008 | Amana PTH123B35AE Air Conditioner
Nov 05, 2013 | GE Zoneline AZ38H12DAD Split System Air...
Jun 09, 2011 | AmcorAire UCHW-H12AF2 Split System Air...
May 26, 2010 | Cfm Daikin R410a Split System Air...
Apr 30, 2010 | LG Art Cool LA121HNP Split System Air...
Apr 15, 2010 | Cfm Daikin R410a Split System Air...
Nov 25, 2008 | GE Zoneline AZ38H12DAD Split System Air...
Jun 07, 2008 | GE Zoneline AZ38H12DAD Split System Air...
414 people viewed this question
Usually answered in minutes!