Question about Goodman CLQ36AR49 Air Conditioner
When my goodman was installed the tech ask if i wanted the blower fan set on high or low speed . my question is for a 1300 sf home which speed is best or what is the benefit of either speed. thanks
Your main concern is the temperature difference across the indoor coil for both heating and cooling. When you turn your thermostat from auto to on, you are on high speed.
If you have long duct runs and little return air registers then high speed
would help cool the house better. However in the heating mode, you
could lose up to 10degrees by having the high speed setting.
What they installed is sized for your house and the speeds should not have to be changed unless the ductwork is not sized right for the house.
Cooling should be High-Black wire.
Heating should be Low-Red Wire.
400cfm equals a ton of cooling= 1200 sq. foot, For cooling you need
High speed. For heating it is whatever the temperature rise across the
coil is, which is located on the furnace/air handler.
Posted on Jul 14, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Sep 02, 2013 | Goodman CKL60AR60 Air Conditioner
Feb 01, 2013 | 1992 Chevrolet C1500
Sep 18, 2017 | Chevrolet Caprice Classic Cars & Trucks
May 12, 2011 | Ruud UAKA037 Air Conditioner
Jan 24, 2011 | Nissan Pathfinder Cars & Trucks
Jan 23, 2011 | Goodman Heating & Cooling
May 01, 2010 | 2003 Saturn VUE
Jan 01, 2010 | Goodman GMS90703BXA Heater
Jul 28, 2009 | Goodman CLQ36AR49 Air Conditioner
217 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: