Question about Frigidaire FAS155K1 Air Conditioner
I have a 1997 Bryant 561c A/C outdoor condenser unit which had the dual capacitor (40/5 370) replaced a few years ago and was running fine. A week ago the condenser fan stopped again so I replaced the cap with the proper replacement but this time without success. The unit is currently turned off at the outside disconnect.
1) When powered up and thermostat at cool, the fan runs at 1/2 speed (~500-600 rpm) but I was getting cool air inside. After 5 mins or so it over heats and shuts down.
2) When the thermostat is off, the fan hums like it is getting some power but does not turn. I need to pull the disconnect to stop it.
3) When I turn the thermostat to "heat", the fan actually turns very slowly in the opposite direction.
I noticed a small spot almost like a gray colored burn on the top of the cap after rechecking the system so I think the new one fried.
It looks like the contactor is operating correctly but I do see some black on the contacts. I tried manually pushing the contacts closed (with an insulated screw driver) and there was no difference.
Any ideas what I should target?
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
check the capacitor of your condenser fan,if busted replace,although thats the common causes of hummimg motor,it can't start,consider also after replacing capacitor still hum,check the motor start winding,and the supply from the source of relay in control panel.have a nice day
Posted on May 08, 2009
SOURCE: CONTACTOR IS NOT MAKING CONTACT
Hello. Make sure you are getting 24 volts to the contactor coil, you can check by using a multimeter and put the probes of the multimeter to each side of the coil ( not the contacts) if you are not getting 24 volts than u must check the low voltage wiring to make sure there is no loose connection. also check the thermostat to make sure it is wired properly.
Posted on Feb 01, 2011
Tips for a great answer:
May 04, 2017 | Bryant Heating & Cooling
Jan 28, 2017 | Bryant Heating & Cooling
May 17, 2014 | Bryant 561CE060-A 561C Package Air...
Sep 27, 2013 | Bryant Heating & Cooling
Aug 20, 2013 | Heating & Cooling
Jul 11, 2011 | Bryant 463AAC008BA Air Conditioner
Jul 04, 2010 | Bryant Heating & Cooling
Jun 22, 2009 | Goodman Heating & Cooling
May 30, 2009 | Bryant 463AAC005BA Air Conditioner
634 people viewed this question
Usually answered in minutes!