Question about Haier Heating & Cooling
It probably needs a capacitor. If you have a voltmeter that will check microfarad, you can check it. You did not say what size unit you have. But the fan is likely a 5 MFD It will say on the old one. The old one probably has 3 terminals on the top and is a cylinder. The top will be marked C, Herm and fan. You can buy a 5 mfd capacitor for about 10 bucks. Run a wire from the C side of the old capacitor to one side of the new one. Remove wires from the fan side of the old one and put on the other side of the new one. Be sure you secure the new one in a place where it cannot short out. Most of the time this can be accomplished with a wire strap.
As always be sure to disconnect the power before servicing. Also disconnect the power on the furnace. This will prevent any damage from occurring to the inside unit.
Posted on Jul 12, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Apr 14, 2015 | Heating & Cooling
Sep 04, 2014 | Heating & Cooling
Apr 14, 2014 | Haier HWR06XC9 Air Conditioner
Jul 23, 2010 | Bryant 463AAC008BA Air Conditioner
Oct 08, 2009 | Haier HC48C1VAR Central Air Conditioner
Apr 20, 2009 | Haier hwr10xc6 Air Conditioner
134 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: