Question about Kohler 12 kW Emergency Power System - 12RES-L
Here is the code explained direct from Kohler's manual. I'd disconnect the generator load first.
UU Undervoltage Shutdown occurs if the voltage falls below 80% of the nominal system voltage for more than seconds. Check wiring and connections.
Reduce the load and restart the generator set. —
Check wiring and Check controller configuration, system voltage
and frequency (parameter UU).
Check AC voltage and adjust, if necessary. 5.7
Replace the SCR module and test voltage again. 4.9
Separately excite unit. 5.2
Check stator continuity
See web site for manual :http://www.kohlerpower.com/onlinecatalog/pdf/tp6196.pdf
Posted on Jul 11, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 11, 2012 | Kohler Electrical Supplies
Aug 16, 2011 | Honda Electrical Supplies
Aug 09, 2011 | Kohler 12 kW Emergency Power System -...
May 28, 2011 | Kohler 12 kW Emergency Power System -...
Feb 04, 2010 | Kohler 12 kW Emergency Power System -...
Jan 17, 2009 | Kohler 12 kW Emergency Power System -...
Oct 09, 2008 | Kohler 12 kW Emergency Power System -...
1,027 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: