Question about Humidifiers
Hi....I recently purchased a house in PEI with a Lifebreath air exchange system, model 200 Max. I do not have a guide on how to set the dial. The manual is more for the installer/contractor. The dial ranges from 20 to 80. I am not sure how to use the dial to control the humidity.
What setting should I set it at in July...and what setting in December, to ensure good air circulation and balance.
Can a wall mount control be installed for this unit. The controls are at ceiling level behind the furnace......................thanks Steve
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You can try installing the water line to your hot water if it is installed on cold line for more humidification. You should make sure your humidistat is up line 6" @least from humidifier for proper humidification measurement.
Posted on Mar 04, 2008
Try turning the water valve going to the soleniod down. There may be too much pressure. You may have to replace solenoid one more time after making the adjustment.
Posted on Mar 13, 2008
No, it is not an accurate statement.
These units have simple configurations They have a water supply similar to a ice making referigerator, an enclosure connected to your supply duct that houses a prop fan and media, a seperate humidistat and a drain for excess water. Your unit may also include fancy controls including an outside thermometer & humidistat to avoid over humidification that can cause problems during freezing weather. The humidistat looks a lot like a thermostat and is located in your living space or in the return duct. The prop fan in the box pulls air from the duct, through evaporation media and back to the duct. An electric solenoid valve releases water that pours over the media.
If the humidiy is below the humidistat seting and the AC/heater is running, the Aprilaire fan starts and the solenoid valve opens. I suspect the facier controls include the flashing warning light.
The warning light spells problem. Aprilaire's customer service should be able to provide guidance for the homeowner in the form of simple checks. I suspect your contractor is avoiding a warentee call and the trip it requires.
A word of caution. These humidifiers can be powered directly from your air conditioning unit control board from an auxiliary connection. If the control board isn't rated to carry the current required by the Aprilaire fan, valve and controls or the Aprilaire encounters and electrical problem, the board can be damaged. This can be avoided by using a relay. The AC board switches a low energy relay. 120 volt house power is connected to load side of the relay and runs the Aprilaire.
My board cooked at a location near this connection, but I can't be sure that the load from the humidifier caused it since four of our neighbors also lost their board. It failed the evening of a snow storm and required a costly emergency after hours service call. The next day a new board required a three hour drive. Fortunately a fan powered propane heater kept our pipes from freezing.
Posted on Oct 07, 2008
SOURCE: lack of humidity
Try the following test, ( I will resume this is a flow through humidifier)
Spray water directly oin the filter make sure it is saturated. Some water should leak from the bottom. After 10 min measure the Humidity to see if this helped. If there is a higher level of humidity the pbm is that not enough water is saturating the filter. Check the level of the filter & water feed nozzle.
Option 2 is to connect the water feed tube to a Hot water source.
Hope this helps.
Posted on Dec 25, 2008
you may try running your blower 100% of the time.this should allow the humidifier to stay on even when your not heating. once the humidity level gets to where you want it, you may be able to put the fan selector back to auto. also you mentioned you have a variable blower. this is great if it is set up to run at approx. 20% fan speed when it is not heating or cooling. at 20% you can circulate enough air through the house to humidify without being able to hear the noise of the blower. it will really increase the comfort level of the house if you tend to have hot and cool spots. if it was not set up this way, contact the installer and ask if they can do this for you.
Posted on Jan 27, 2009
Tips for a great answer:
Dec 25, 2015 | Kenmore Cool-Mist Ultrasonic Humidifier...
Mar 08, 2015 | Carrier Humidifiers
Apr 01, 2011 | Vicks Warm Mist V745A 1 Gallon Humidifier
Feb 20, 2011 | Honeywell HE360A1027 Whole House...
Jun 20, 2017 | Aprilaire 700 Humidifier
Nov 17, 2010 | Aprilaire 700 Humidifier
Mar 01, 2010 | Sunbeam Ultrasonic Humidifier
Dec 27, 2009 | Aprilaire 550 Humidifier
Jan 16, 2009 | Honeywell Power Humidifier: Furnace...
Dec 28, 2007 | Honeywell HE220A1019 Whole House...
227 people viewed this question
Usually answered in minutes!