Question about Carrier Heating & Cooling
Can anyone point me in the right direction to solve this issue.
I have a Carrier AC/Heat pump with a totaline thermostat. Heat comes on when the temperature setting calls for cool.
The airhandler model is FY4ANF030, the compressor is 25HBA33OA003, and the Totaline thermostat is a P474-0100.
It was working fine and is about 4 years old.
Getting heat in the cooling mode leans toward the reversing valve in the outside unit. it changes the flow of refergerint so that the hot air you get outside in the summer is blown inside in the winter. another possibility is that the reversing valve isn't getting 24v check to see if you have 24v at O and C either at the t-stat, furnace, or the outside unit. if you check at the furnace rember the safty switch for the lower door if that switch is open you will have no power. i would look at the t stat first if you have 24v there go to the outside . 24v present outside will mean a bad valve or board, no 24v means a bad or broken conection in the control wire between the stat and the outside unit(usally the orange wire)
Posted on Jul 11, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 13, 2017 | Carrier Heating & Cooling
May 13, 2014 | Carrier Heating & Cooling
Nov 11, 2013 | Heating & Cooling
May 28, 2012 | Carrier Totaline P291-1003 Capacitor 10mfd...
Aug 08, 2011 | Heating & Cooling
Feb 20, 2010 | Heating & Cooling
Jan 27, 2010 | Heating & Cooling
May 06, 2009 | Heating & Cooling
Dec 20, 2008 | Carrier 38BRC048 Air Conditioner
Nov 25, 2007 | Honeywell CT3600 7 Day Electronic...
363 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: