Question about Cooper Industries Cooper Wiring 274W Switch and Outlet
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
one of the white wires has power on it constantly....that wire connects to the black wire of the leviton.......the other white wire which has no power to it is going to whatever needs power so that wire connects to the red wire of the leviton....the green wire connects to the metal box where your mounting the leviton.
Posted on Jun 28, 2010
First, turn off the power to this circuit to avoid getting a shock.
If the two devices that are controlled by the combination switch are lights, you will want to join the two (2) white (neutral) wires together with a wire nut, as these are not connected to the switch.
You also want to connect the bare copper wires (ground) together and connect one of them to the switch's green grounding screw and IF the wall box is metal, you also need to attach the ground wire to the box with a green grounding screw.
Now, you can connect the wires that go to your lights, the red and black wires that are part of the same wire and are routed to the same location thru the wall box. Take either the black or red and connect them to the screws on the side of switch that are not connected together with the small brass strip between them. Put the red on one of these screws and the black on the other.
Now with the black wire that is the hot (Common), this is the one that is bringing power into the wall box, should be connected to the other side of the switch, the one with the two (2) screws that are joined together with the brass strip between them.
This will allow you to turn on and off each of the lights (or a fan, etc) separately with each switch sharing the common power source.
Here's a picture of the switch that shows the side of the switch with the common side and the brass strip that connects the screws together. This is the side where the one black (hot / common) wire that supplies the power gets connected.
You can also open up the box the switch came in and you'll find a wiring diagram for the switch that illustrates how to properly wire the switch for your application.
I hope you find this Very Helpful and best regards!
Posted on Oct 10, 2009
remove white switch one and connect to incoming white ground--all whites should be connected [hooked] together these are grounds-- switch 1 black from fan ,leave switch 2 red from fan ,switch 3 vanity black
Posted on Feb 22, 2010
SOURCE: not sure how to wire this switch
Switch will have a commom terminal that the hot wire connects to.
The other three terminals are for the devices -- light, fan and other device.
The white wires should be the grounded wire returns for the circuits unless they are identified by color tape to be hot line side of power.
Be careful of the grounded side of circuit, can shock or kill, treat all wires as being energised. If you are not sure, use a electrical tester,
or get help.
Posted on Jul 22, 2010
SOURCE: We are trying to install
You are installing a combo device with switch and outlet.
The outlet is tamper resistant so a child cannot stick a key into outlet and get shocked.
For the outlet to work, a 2-prong plug must be inserted.
Wiring the device:
Electricians don't guess, they test.
Device has different colored screws: dark, silver and brass.
Separate wires for testing.
Do not unwind wires that are twisted together.
White wires that are twisted together and located in back of box are included in testing.
Use ordinary 2-lead tester.
Tape tester leads to wood sticks to keep hands away from power.
Turn power ON.
Test each wire to bare ground wire.
Tester lights up on Hot wire. This wire connects to dark screw.
Hot is identified.
Test Hot wire to all other wires, except bare ground wire.
Tester lights up on Neutral wire. Neutral connects to silver screw.
If you do not have a Neutral wire, then outlet will not work for that location.
You can get the outlet to work by connecting bare ground to silver screw, but that is violation of code.
Last wire goes to Load (light, fan, motor).
Load wire connects to brass screw.
In your case, this is red wire.
Add a comment for more free help.
Also take advantage of fixya phone service.
For a price, expert speaks with you over phone while you work on switch or any do-it-yourself project.
Fixya is always less expensive than a service call.
Posted on Jan 19, 2011
Tips for a great answer:
Nov 01, 2014 | Car Audio & Video
Aug 30, 2014 | Leviton 5634 Dual 1 Pole Switch Decora...
Jun 29, 2011 | Leviton R01-PR180-1LI Decora 180 Degree...
Feb 27, 2011 | Leviton COMBINATION SINGLE POLE TOGGLE...
Feb 27, 2011 | Leviton 8299 Combination Switch / Smart...
Feb 24, 2011 | Leviton 5634 Dual 1 Pole Switch Decora...
Feb 01, 2011 | Cooper Industries Cooper Wiring 274W...
Jan 19, 2011 | Leviton 8299 Combination Switch / Smart...
Feb 22, 2010 | Leviton 003-1755-W Three Rocker Switches
Sep 02, 2009 | Leviton Decora Combination Switch - 5625-I...
903 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: