Question about Raypak Rp2100 Pool & Spa Heater Lonox 407k Btu Natural Gas Polymer Header Digital Rp407aenc
I have a Raypak RP 2100 R405 pool heater. When I turn the rocker switch on I get nothing or no lights on the control panel and nothing happens to the heater. I checked and there is power going from the transformer via the blue wire to the PC board but no power being distributed to anywhere else. Is it the PC board and if so how can I check to verify this is problem. The board is expensive and they no one will return it if this isn't the problem.
Yes its faulty PC board.As no Power Coming from the board.Click this link directly to get PC board.
To confirm the fault in PC board.
Check for exact 24 volts on PC board.
One yellow and One Blue wire.
For checking transformer check
120/240 volt to transformer(time clock circuit breaker wire connections).
Thanks. Keep updated for any more query. You can rate this
solution and show your appreciation.
Posted on Jul 10, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jun 01, 2014 | Raypak Pool & Spa
Aug 05, 2013 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
Jun 16, 2012 | Raypak 130,000 BTU Natural Gas Pool...
Jun 11, 2012 | Raypak Free Hydraulic Lift Gate Delivery -...
Jan 02, 2012 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
May 31, 2010 | Raypak Free Hydraulic Lift Gate Delivery -...
Sep 16, 2009 | Raypak Pool & Spa
Jul 05, 2009 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
563 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: