Question about Goodman CLQ36AR49 Air Conditioner
I cant get the airconditioner to keep my little business of 800 sq ft cool. Yesterday it was 86 in our rooms.
You need to check that tour filters are new. Then check that air is coming from the vents and is at least 15 degrees cooler than room temp. If no air coil is frozen, or blower motor and run cap are not working. If frozen than turn system to off and fan switch is on until you feel air through vents.
You'll need to make sure the outside unit is runing and the larger copper line is cold like a can soda. If it's cold but is freezing up, it needs to have a charge added. If its running but not cold and the fan is not running or the compressor isn't running it could have a blown capacitor. If its not running at all check. the circuit breakers and reset them. And a good idea to keep the outside unit washed with water,and that it is clear of weeds and stuff.
Posted on Jul 10, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 12, 2014 | Goodman Heating & Cooling
Jun 02, 2014 | Emerson Quiet Kool 12HT13 Air Conditioner
May 28, 2014 | Computers & Internet
Aug 05, 2011 | Maytag M6Q10F2A Air Conditioner
Aug 05, 2011 | Danby DPAC12031 Air Conditioner
Aug 03, 2011 | Heating & Cooling
Jun 07, 2011 | Maytag M6X08F2D Air Conditioner
Sep 10, 2009 | SoftMath Algebrator - Algebra Homework...
Jun 11, 2008 | LG Heating & Cooling
156 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: