Question about LG BG8000ER Air Conditioner
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
It sounds to me like the compressor is overheating and tripping on internal or external overloads. After the unit cools down again it will try to run for a little while. Then this cycle would start over. I would check the condenser coil for dirt and filth. This portion of the unit may be on the out and backside of the unit. You should at least be able to see light through the coil.
I believe the thermistor that you removed temporarily is used for a freeze situation. I do not believe that it is your problem. Good luck:)
Posted on Jun 18, 2008
NGFAM! Happy to assist you!
Sounds like the freon is low therefore it will not or stay on!
My words alone can not help you fix the unit!
You need service!
Let me know how it goes??
Please give me a good rating here at fixya.com before you sign off!
PLEASE GIVE ME A GOOD RATING HERE AT FIXYA.COM BEFORE YOU SIGN OFF
Posted on Aug 29, 2008
Check that the fanmotor can spin freely. If not, can be caused by seized bearing on left side of fanblade, or foreign object, insect nest stuck in fanblade. If however it spins freely, check that fanmotor is being supplied with voltage (you sound technically capable of operating a volt meter). If power is supplied, fanmotor is faulty and needs replacing. If no voltage, problem lies with the pc board. If you know someone who is capable let them check the relays on the board. Also you can check that all plug on connectors are making good connection.
Posted on Mar 05, 2009
Remove the front cover of the unit to expose the cooling coil. Put the unit on and observe if there will be formation of frost (ice) on the coil. If there's frost formation, the common cause is dirty cooling coil. Have it cleaned using an alkali base coil cleaner. If the coil is clean, then the problem is the fan motor. It might be turning slow due to copper loss. Have it replaced.
Posted on May 29, 2009
Tips for a great answer:
Aug 06, 2013 | LG Heating & Cooling
Mar 30, 2013 | LG Heating & Cooling
Jul 23, 2011 | LG Heating & Cooling
Apr 26, 2011 | Briggs 491588 and Stratton Original Air...
Apr 19, 2010 | LG LB1200ER Air Conditioner
Sep 20, 2009 | Dryers
May 28, 2009 | LG Heating & Cooling
95 people viewed this question
Usually answered in minutes!