Question about Heating & Cooling
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
If the compressor is tripping the breaker, then its 1 of 2 things. First clean the coils and change the air filter. If the coils are dirty and/or the filter is clogged, it will make the compressor overload and the high amp draw will make the breaker trip. If this doesn't solve the problem, you need to check the compressor itself. remove the connections at the compressor, leaving only 3 posts on it. You will need a meter to check for continuity to all 3. They should all have continuity to each other. While there check the wires. Sometimes a burnt wire will come off and arc on something causing the breaker to trip, if you are lucky.
Posted on Mar 02, 2008
SOURCE: No cold air.
Is the air conditioner completely dead? See section 1. Is the thermostat knob turned to the proper setting? Is the compressor motor running? The compressor is a football-sized case with no apparent moving parts. It is located inside the air conditioner at the center. Is it humming or making any kind of continuous noise or causing the lights to dim? If it is making a continuous noise, and your air conditioner is still not cooling at all, there may be a serious problem with one or more of these areas:
If the compressor is not running but you do have power to the air conditioner there may be a problem in one or more of these areas:
Posted on May 26, 2009
Here is a tip about trouble shooting your air conditioner...
Air Conditioner Trouble -Review the Possibilities
Posted on Jul 12, 2010
Tips for a great answer:
Jun 10, 2014 | Frigidaire FAC107P1A Wall/Window Air...
Jan 11, 2014 | Whirlpool ACP102PS Portable Air...
Aug 24, 2011 | Ruud UAKA030 Air Conditioner
Jul 24, 2011 | Heating & Cooling
Aug 27, 2010 | Coleman Mach 15 Air Conditioner
Jun 06, 2010 | Samsung AW0503B Air Conditioner
Jun 02, 2010 | Bryant 463AAC005BA Air Conditioner
Mar 16, 2009 | Dometic Rooftop RV Air Conditioner
Jun 30, 2008 | Heating & Cooling
59 people viewed this question
Usually answered in minutes!