Question about Ruud UBHC Air Conditioner
Have you check the outside breaker box? If thats not it then its probably the contactor.
Posted on Jul 09, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
It sounds like your condenser fan motor may be locked up or the capacitor that helps give the condenser fan motor a kick to get it started may be defective. Try turning your system on and using a long screwdriver try to push the fan blade on the condenser fan motor to see if it will run normally if you give it the starting boost it needs.If it does run at full speed and doesn't over heat or start and then slow down then you probably only need to replace a simple 10-12$ capacitor. If it barely turns, makes an odd humming sound or overheats etc. then you will have to replace the condenser fan motor. This is assuming that the outdoor condenser has the 220v supplied and the 24v supplied to the compressor relay, that the compressor relay is engaged and suppling 220v to the condenser fan motor.
Posted on May 30, 2008
Tips for a great answer:
May 20, 2014 | Ruud Heating & Cooling
Nov 25, 2012 | Ruud Matching Split Air Conditioner
Aug 08, 2012 | Ruud Matching Split Air Conditioner
Aug 06, 2012 | Ruud UBHC Air Conditioner
Aug 12, 2011 | Heating & Cooling
May 02, 2011 | Heating & Cooling
Aug 24, 2010 | Ruud Matching Split Air Conditioner
Jan 10, 2010 | Ruud Matching Split Air Conditioner
May 28, 2008 | Ruud Matching Split Air Conditioner
921 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: