Question about Goodman Heating & Cooling
Is your condensor fan motor stopping for any reason while calling for cool? no mention of how old unit is ? many times the fan may run for a few minutes or 30 min. or what ever amount of time then trip on internal overload. Check to see if you have a lot of dirt blocking the bottom of the ventilated condendsor motor if so blow out all vent holes on motor and oil motor if equipt.Double check the compressor terminal hookups for burnt wires remove clip and look at the 3 wires ,are they tightly on the compressor and not rusted and loose.The thermostat and temperature sensor is not functioning properly.As it should come on when there is temp rise but they are not functioning properly so the ac is not coming on.
Posted on Jul 09, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 01, 2014 | Goodman CLQ36AR49 Air Conditioner
Feb 11, 2011 | Goodman Heating & Cooling
Jan 30, 2010 | Goodman GMS90703BXA Heater
Jun 10, 2009 | Goodman CKL30AR30 Air Conditioner
Jan 20, 2009 | Goodman CLQ36AR49 Air Conditioner
Jan 18, 2009 | Goodman CKL49AR49 Air Conditioner
17 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: