Question about Culligan Under Sink Water Filter
Have the TDS or total dissolved solids tested. A good reading is 10% of the ifluent water. For example if the incoming TDS is 300parts per million, the product TDS should be 30ppm or lower. If it is higher than that, replace the membrane. Any local water treatment dealer should be able to locate and replace it for you.
Posted on Jul 21, 2010
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 18, 2014 | Hagen Laguna Clearflo 700 Kit - Includes...
Sep 27, 2011 | Karcher 2500 PSI Pressure Washer
Jun 14, 2011 | Hoshizaki Freezer Commercial Ice Machines...
Nov 07, 2010 | Culligan Under Sink Water Filter
Oct 22, 2010 | Computers & Internet
Aug 03, 2010 | Toto MS950CG-12 Neorest 500 Elongated One...
Jul 08, 2010 | Culligan Sales #SY-750S Under Sink Water...
Apr 02, 2009 | KitchenAid KSRS25IL Side by Side...
May 26, 2008 | Bosch Classixx WFL 2066 Front Load Washer
110 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: