Question about Goodman CKL60AR60 Air Conditioner
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You should be able to move the reversing valve wire from O terminal, (the changeover relay), on the thermostat to B terminal. I deal mostly with York
which O on the t'stat is normally open and B is normally closed.
Posted on Oct 06, 2009
SOURCE: Replacing a Rheem Heat Pump
The difference is that the reversing valve is energized it heat mode for one brand and energized in the cooling mode for the other brand. An "O" on the circuit board indicates energized in cooling and a "B" on the circuit board indicates energized in heating.
Posted on Sep 09, 2010
Tips for a great answer:
Oct 02, 2015 | Goodman Heating & Cooling
Jul 25, 2014 | Goodman Heating & Cooling
Feb 01, 2013 | Goodman Heating & Cooling
Oct 28, 2011 | Goodman GMS90703BXA Heater
Aug 14, 2009 | Goodman CKL60AR60 Air Conditioner
Jul 12, 2009 | Heating & Cooling
May 29, 2009 | Goodman CLJ30AR32 Air Conditioner
Jan 27, 2009 | Goodman GMS90703BXA Heater
Jan 16, 2009 | Goodman PHKJ048-1 Air Conditioner
Sep 21, 2008 | Goodman Heating & Cooling
377 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: