Question about Ruud UBHC Air Conditioner
Posted by Anonymous on
When you say drip pan are you refering to a pan located under unit in case drain plugs ? If this is what you are talking about and you have a furnace that is 90% efficient or more which will be vented with pvc, it needs to be under the whole furnace as condensate water also comes from furnace when operating and if this drain plugs you will also have water leaking down from furnace. If it is a 80% furnace which will be vented into a chimney then pan needs to be just under a/c
Posted on Jul 08, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 26, 2014 | Goodman GMS90703BXA Heater
Nov 30, 2013 | Amana AER3311WAW White 4.8 cu. ft....
Oct 07, 2013 | Heating & Cooling
Apr 26, 2017 | Ruud UBHC Air Conditioner
Jul 11, 2011 | Goodman CLQ36AR49 Air Conditioner
Jun 13, 2011 | Intertherm Heating & Cooling
Jun 24, 2010 | Heating & Cooling
May 23, 2010 | Ruud UBHC Air Conditioner
Aug 03, 2009 | Coleman Heating & Cooling
May 11, 2009 | Heating & Cooling
280 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: