Question about Heating & Cooling
YOU MUST HAVE THIS THING CHECKED OUT BY AN EXPERT. IT IS A FIRE HAZARD. Even if the thermostat was a closed circuit, the furnace would be working all of the time but it would not be overheating to the point of warping parts. You are either overfiring or your blower is not running all of the time. If it's a blower problem, clean out the dirt and dust and oil the motor. If the motor is not running, replace the fan control or the motor. If the furnace is overheating, your gas regulator might be bad allowing to much gas pressure to the furnace. Also, make sure that the burner orifice's are the correct size for the heater.
Posted on Jul 08, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 05, 2015 | Vulcan Heating & Cooling
Jun 11, 2011 | Heating & Cooling
Apr 11, 2011 | Empire Direct Vent Wall Furnace;...
Nov 06, 2010 | Dayton Gas Furnace Heater
Oct 05, 2009 | Heating & Cooling
Mar 29, 2009 | Vulcan Heating & Cooling
Sep 26, 2017 | Honeywell Heating & Cooling
528 people viewed this question
Usually answered in minutes!