Question about Ruud UBHC Air Conditioner
I was weed eating yesterday and I got tangled in what looked to be the wires that go to the thermostat, well needless to say my AC shut down and once I hooked the wires that I cut back up still a no go, I checked under the house and followed the wires all the up and to the thermostat and it is fine, there are actually spots where it is zip tied off to prevent to much tension, there is what looks to be a momentary test button on the side of the AC under the electrical panel and when I press it the fan kicks on, but like I said it is momentary. I also took apart my thermostat to see if anything was fried and it looked OK too. I deal with car electronics all day (i know not completely the same but) I know what a bad electrical board looks like. Either way, all the breakers are good and are not popped so I don't know where else to look.
Check on the board and see if the 3amp fuse is blown,if you do not have
a fuse in this board, then check for 24volts between R and C, if you do
not have voltage there your transformer is blown, it will also have a bad
burnt smell if it happened
Posted on Jul 17, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 30, 2012 | Carrier 38CKC060 Air Conditioner
Oct 03, 2011 | Dometic 57915531 Air Conditioner
Sep 12, 2010 | Heating & Cooling
Aug 23, 2009 | Ruud UAMB042 Air Conditioner
Jun 05, 2009 | Ruud UPMC036 Air Conditioner
Jun 05, 2009 | Intertherm P3RA-048K Air Conditioner
May 07, 2009 | Intertherm P3RA-030K Air Conditioner
Apr 22, 2009 | Goodman CKL24AR24 Air Conditioner
Jun 27, 2008 | Goodman CLQ36AR49 Air Conditioner
Dec 24, 2007 | Intertherm P3RA-048K Air Conditioner
42 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: