Question about Heating & Cooling
Assuming that the 2 systems are isolated, that there isn't any cross over between the systems...
It is normal for an air conditioner system, from window unit to central, to be able to circulate the air, even if not cooling. This is known as Circ or Fan Only Mode. But, in this mode, the outside unit (condenser) would not be turned on.
Since the condenser for downstairs has its fan blowing, the compressor, as you properly surmised, is not running. There would not be anything in the attic exchange that would affect this, since you are in cooling mode, and not using the furnace.
Some possible reasons for the compressor to not run are: Overload Protection is tripped (burned out), Compressor contactor (high current relay) is not engaging or contacts / coil are open, Wiring between downstairs Thermostat and condenser is damaged (in particular, the wire that activates the contactor). A failed compressor protection (time delay) device will also prevent it from starting / running.
Time to call a service tech.
Posted on Jul 08, 2010
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 30, 2013 | Heating & Cooling
Feb 20, 2012 | Goodman Heating & Cooling
Dec 20, 2010 | Goodman GMS90703BXA Heater
May 17, 2009 | Heating & Cooling
Apr 26, 2009 | Carrier 38CKC036 Air Conditioner
Apr 25, 2009 | Heating & Cooling
Jun 04, 2008 | Goodman CLQ36AR49 Air Conditioner
61 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: