Question about Coleman Mach III Air Conditioner
TEMPERATURE OF AIR IS LESS COMING OUT OF UNIT and Takes longer to cool down ... air condition guy sez it is a sealed unit and cannot be recharged??? ... ALL NEW FILTERS ETC ETC..
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Recharge My AC Unit
The system needs to be accessed through what is call a tap valve. After a tap valve is in place a high vacuum should be pulled on the system down to 500 microns to remove air and non condensible gases along with any moisture from the system. Then the charge should be weight into the system according to the name plate with the proper type of refrigerant, generally Refrigerant 22. An alternate method is to charge the system by superheat of the gas returning to the compressor. Ambient temperature determines how high or low the superheat should be.
Posted on Jun 20, 2008
Tips for a great answer:
May 10, 2014 | Coleman Mach 15 Air Conditioner
May 18, 2012 | Coleman Mach III Air Conditioner
Aug 29, 2010 | Coleman Mach 15 Air Conditioner
Aug 27, 2010 | Coleman Mach 15 Air Conditioner
Jun 29, 2010 | Coleman Mach 15 Air Conditioner
Aug 08, 2017 | Coleman Mach III Air Conditioner
686 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: