Question about MGE UPS Pulsar Evolution 2200 UPS System
Posted by Anonymous on
Prag board(main board ) not working properly . Replace the board to solve the problem.
Posted on Jul 19, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 18, 2012 | Computers & Internet
1 - Press the "0" button (28) more than 3s. The buzzer beeps once, and the load is no longer protected by the UPS. It is powered via the Normal AC source. If the UPS is set in frequency converter mode, the equipments will not be powered. If the Normal AC source is out of tolerance, the UPS will generate a 10ms output calibrated break. 2 - For a full shutdown of UPS and connected load, the upstream circuit breaker (notincluded) should be set to the "0" position.
Sep 09, 2011 | MGE Pulsar MX 5000 (68505) UPS System
Feb 16, 2011 | MGE UPS Pulsar EXtreme 1500 C UPS System
Sep 15, 2010 | MGE UPS Pulsar Evolution 1500 UPS System
Jun 14, 2010 | MGE UPS Pulsar Evolution 2200 UPS System
Jan 05, 2010 | MGE Pulsar M RT 2200VA 3U UPS Hotswap IEC...
Aug 13, 2009 | MGE UPS Pulsar Evolution 3000 UPS System
Jun 05, 2009 | MGE UPS Pulsar Evolution 3000 XL (89349)...
Sep 19, 2015 | MGE UPS Pulsar Evolution 2200 UPS System
Jun 01, 2012 | MGE UPS Pulsar Evolution 2200 UPS System
308 people viewed this question
Usually answered in minutes!