Question about Heating & Cooling
I need more info. I can't seem to find your indoor unit. Is this a 2 stage cooling unit or just 2 speed fan? Please send the model number of your indoor unit.
Posted on Apr 11, 2017
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The Mitsubishi units have to be reset by turning off the indoor units by switching the remote or thermostat to off. Then turn off the breaker to the outside unit(s). After 30 seconds,turn on the breaker and then you can turn on the remote for cool. If no lights come on on the inside units, most likely you have blown a fuse soldered on the main PC board. At this point, call your technician. A goos tech will be able to wire in an in-line fuse holder so if it should happen again, you can easily replace the fuse. If you do see a light or two come on at the indoor unit but the outdoor unit does not start after 3 or 4 minutes, sounds like you will need to call a technician. Most likely you have a blown fuse on the main PC board of the outside unit. It is not an easy one to replace. Good Luck!
Posted on Sep 04, 2007
SOURCE: coleman rv a/c
It is definitely with the compressor. It should more like you may have a weak winding in the compressor, you can a hard start capacitor (sp5 ) that will help the compressor on restart. Note that this is a last chance solution for a compressor.
Posted on Oct 01, 2008
are you speaking of the outside fan or inside? compressor should be a little warm but not boiling hot. the unit could be low on freon. if low it will run a while but the compressor will overheat and shut off leaving the fan running by itself ouside. if nothing outside is running check power. if you have power check the contacted outside to make sure it's pulled in. contacters are bad about going out on goodman untis. Also ants can get under contacts.
Posted on Jun 18, 2009
be aware that not repairing this asap that you are causing yourself more problems First I would change out the fan capacitor and see if this could be the problem. Secondly if the capacitor isn,t the problem change out the motor . By continuing to allow the system to cycle like this the compressor will take a dive on you costing more . Good Luck
Posted on Aug 04, 2009
Testimonial: "Yes, it's dual run capacitor problem. I used a stick to spin the fan blades and it starts to slowly spin and up to normal speed, so motor is good."
Tips for a great answer:
Dec 07, 2015 | Cars & Trucks
Jul 18, 2015 | Frigidaire FAH105N1T Air Conditioner
Jun 25, 2015 | Dehumidifiers
Jan 18, 2015 | Pentair Pool & Spa
Jan 30, 2014 | Lenovo MTQ45NK Motherboard Desktop Board...
Feb 09, 2013 | 2005 BMW 545i
Feb 06, 2010 | Omega Keeprite Furnace Flue Exhaust Venter...
Jul 05, 2009 | Heating & Cooling
Jun 15, 2009 | Hampton Bay 24750 Huntington III Ceiling...
105 people viewed this question
Usually answered in minutes!