Question about Amana Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: not turning on
Try to reset the unit by disconnecting the power supply for 10sec. and operate the unit. If it wont work replace your Room Air and Coil Thersmistor or test the thersmistor with mulitester. The resistance reading of thermistor is 10 kilo ohms @25deg. C room temp. If it is shorted or open the unit wont operate.
Hope this can help :)
Posted on Jan 08, 2009
Where is water dripping? Out the outside unit or inside? Evap. Coils (indoor coils) condense when cooling so it is necessary to have a condensate drain hooked up. If the unit is leaking out of something besides the drain like out of the coil case then you have a blockage in your condesate line either in the drain pan under the coil or somewhere in the line that leads to your drain. blow the line both ways with nitrogen or pull the line out and clean it with a hose.
Posted on Jul 29, 2009
5 flashing is ' compressor drive' and check the high pressure, condenser fan motor capacitor for proper running
Posted on May 21, 2010
Tips for a great answer:
May 31, 2014 | Samsung Indoor Split Type Room Cold Air...
Sep 18, 2010 | Intertherm Heating & Cooling
Sep 13, 2010 | Carrier BCA101R Air Conditioner
Apr 18, 2010 | Friedrich MR18Y3F Split System Air...
Mar 30, 2009 | Carrier 38CKC042 Air Conditioner
Feb 02, 2008 | Heating & Cooling
Dec 22, 2007 | Carrier 38CKC036 Air Conditioner
367 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: