Question about Heating & Cooling
Hello there, I have two Goodman AC units for my home. The one that is not working is a CPLE36-1C. When I turn up the AC for that unit, I noticed the fan on the unit outside does not work. I could feel that the fan motor is getting warm/hot, but the fan does not spin. What could be the problem? Would I need to replace the fan motor? Or could it be something else? thank you. tim t
Hello Tim First Turn the power off! Try to turn the fan blade with a twig or something.Is it tight ? It should turn freely.If yes open the cover where the wires connect & check if the capisitor is expanded or leaking if so replace that with the SAME one (uf value&volts).Check for burnt wires also.The capicitor is a round or oval shaped can (looks like a large battery) with wires cliped/pluged in on top.Next let the motor cool off 1 hour and restore power.Does it BUZZ for a short time then stop?If yes its new motor time.Good luck
Posted on Jul 07, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 14, 2014 | Goodman CLQ36AR49 Air Conditioner
Aug 04, 2012 | Goodman CKL36AR36 Air Conditioner
Aug 29, 2011 | Goodman CKL42AR42 Air Conditioner
Aug 19, 2011 | Goodman CLQ36AR49 Air Conditioner
Aug 04, 2011 | Goodman Heating & Cooling
May 30, 2011 | Goodman Heating & Cooling
Aug 30, 2010 | Heating & Cooling
Jun 26, 2009 | Goodman Heating & Cooling
Jun 07, 2009 | Goodman CKL24AR24 Air Conditioner
366 people viewed this question
Usually answered in minutes!